for Carroll, OH
outstanding quick service
Robel - Carroll, OH
great business/ great technician and quick help
Extremely professional, courteous and efficient.
Bill - Carroll, OH
quality service and good staff
Duane Stagge - Carroll, OH
Ernie - Carroll, OH
Chris - Carroll, OH
Energetic, Super Polite, Hard working, No pressure, good info on the furnace tuneup and diagnostic.
Great service. fair price.
Duane - Carroll, OH
Furnace is almost 29 years old and A/C is 14 years old. The part to repair the furnace would have cost about $800.00. It was not worth repairing the furnace as it would probably have more issues in the future. Replacement of both units was pretty much a no brainer.
Robert - Carroll, OH
They were promt, nice and trouble shot my furnace in a timely manner. He ordered my part and tomorrow it will be fixed. I called them and they were at my house in a couple of hours. Very fast.
Rick - Carroll, OH
Found zone board transformer bad replaced with new transformer all lite up and began to run. This home has 1 master stat with 3 sensor stats. Zone 4 has neen disconnected but all other zones are functioning properly in turning in and off with 3 wire to all zones. Zone panel has a 10 amp fuse in it which then popped the furnace board transformer and the zone board transformer.
Pre season tune up/check out on a TEMPSTAR brand furnace. If leaking continues after todays repair. Need to replace plastic base and run a new piece of 2in PVC through the gasket as a solid piece. Recommend bringing 2in and 3in fittings w/pipe if we need to return.