for Carroll, OH
outstanding quick service
Robel - Carroll, OH
great business/ great technician and quick help
Extremely professional, courteous and efficient.
Bill - Carroll, OH
quality service and good staff
Duane Stagge - Carroll, OH
Ernie - Carroll, OH
Chris - Carroll, OH
Energetic, Super Polite, Hard working, No pressure, good info on the furnace tuneup and diagnostic.
Great service. fair price.
Duane - Carroll, OH
Furnace is almost 29 years old and A/C is 14 years old. The part to repair the furnace would have cost about $800.00. It was not worth repairing the furnace as it would probably have more issues in the future. Replacement of both units was pretty much a no brainer.
Robert - Carroll, OH
They were promt, nice and trouble shot my furnace in a timely manner. He ordered my part and tomorrow it will be fixed. I called them and they were at my house in a couple of hours. Very fast.
Rick - Carroll, OH
Pre season tune up/check out on a TEMPSTAR brand furnace. If leaking continues after todays repair. Need to replace plastic base and run a new piece of 2in PVC through the gasket as a solid piece. Recommend bringing 2in and 3in fittings w/pipe if we need to return.
Diagnostic Service Call on NORTEC furnace at rental property. Outdoor unit is running. Vapor line is frozen. Outside unit is an Air Conditioner and NOT a heat pump, it contains no heat pump components. Inside unit is electric, thermostat is a heat pump thermostat. - Unit was running both heating and cooling together because the thermostat was programmed to run a heat pump. Because the unit is not a heat pump outside, when it is called to run by the thermostat the heat pump it will turn on only in cooling. Replaced the heat pump thermostat with a regular thermostat. Unit is operating in heating, though struggling without the assistance of a heat pump unit.