for Johnstown, OH
Found 2 spots that are leaking on coil. Customer wants Puron added and a new evaporator coil put in. Trying to add Puron and high pressure spiked to 467. After doing some research and looking at other pressure related numbers, I have come to the conclusion that the TXV has failed also. Also wants estimate on a system for upstairs. Total for new evaporator coil and Puron is $3336
2013 Carrier AC not cooling. Found 24 volts across all terminals on control board and 120 v at blower. Blower has no amps and is not turning. Failure of blower has caused evap coil to freeze, then melt in to cabinet. Furnace control board has scarring and damage. Since under warranty, advised replacing to avoid issues down the line.
Replaced Spacegard Air Cleaner Media filter for a Johnstown customer.