for Lancaster, OH
Jesse - Lancaster, OH
Our AC went out and it was 83 in our house, so we were desperate. Our tech showed up on time and was very friendly and knowledgeable. He had our AC fixed within an hour!
Very helpful, Great service !!
Chambers - Lancaster, OH
He was here on time !! Very helpful with our questions !! Would highly recommend !!
Cory is THE BEST!!
Marti - Lancaster, OH
After experiencing the aftermath of a water leak, floors ripped out, boxes piled everywhere, deafening fans and dehumidifiers running, Cory was the only technician that bothered to put on booties before walking into our house. Cory was knowledgeable and informative. All of our concerns about possible water damage to the furnace were addressed. Any questions were answered. I was impressed with my overall interaction with Canal Winchester Heating and Cooling. They answered the phone when I called, many did not, or did not return my call when I left a message. They were accommodating, came on a Saturday, called to advise they were on the way. 5 Stars I highly recommend!
Rita - Lancaster, OH
Very nice employees
shows caring attitude and freindly
Ogg - Lancaster, OH
Parmley - Lancaster, OH
got next morning service. prompt and fixed problem.
Furnace tuneup and safety inspection on Carrier furnace. All checks are good and the equipment is running properly.
Upon arrival I found a Trane unit not working. LED code giving normal operation alert. Had to jump in to heating mode by connecting R to W. After a few minutes of running, breaker tripped. Reset breaker and furnace, able to get it to run again. Checked and had 27 volts at R and common, and 28 from R to W. After a few seconds though, the voltage on W to R dropped to 13 volts and from R to C it dropped to 8 volts. The blower motor was also showing signs of struggling to work. Combustion test showed 13 ppm, 2.5 C02% and 15 O2% . I suggests replacing board to to voltage inaccuracies, but is concerned that blower motor would also need replaced. Due to age of system, 1993, I do not recommend replacing parts. Customer wants to go with new furnace.