for Gahanna, OH
Tracey - Gahanna, OH
I completed a Full Install of a Carrier 96% Variable-Speed Two-Stage Gas Furnace 59TP6 (Up to 100,000 BTU) Honeywell T6 Programmable Thermostat/Emerson 1F85U Carrier 17 SEER Two-Stage Air Conditioner 24ACB7 (Up to 3 ton) The system is operational upon departure.
I found the 2012 York gas furnace locked out on code 8 (ignition lockout due to too many flame recycles). I reset furnace and cycled system on. I pulled and cleaned the flame sensor. Recommended to customer to change filter. No other issues at this time.
I am Performing our Five Star Tune-Up & Safety Check on a 2000 Payne Gas Furnace. All readings were within manufacturer's specifications, unit operating properly at this time.
Upon arrival found AC unit not turning on and Thermostat blank. Found 3 amp fuse blow, replaced fuse and unit worked when calling for heat. The outside unit I found a blown capacitor, replaced and still blew fuse. Will need to go back and run 24 volt wires to outdoor unit.